CommunicationWe are always trying to improve our products especially due to the feedback from our customers. Based on battery communications with Victron inverters and a large number of notifications towards the inverter, we have revised the product and recommend to use the VE-SHUNT-BT-500 for battery management and SOC measurement. Please read the User Manual for more information.
Product descriptionThe energy storage is based on LiFePO4 batteries with integrated Battery Management System (BMS) and short-circuit protection. Power output is 48V 100A (5 kW), communication output is CAN and RS485. The outputs are on both sides of the box. The individual 5 kW modules can be scaled with system power and communication connections up to 12 units (master + 11 slaves). This increases the storage capacity up to 60 kWh, but the resulting output power and voltage remain the same - 5 kW /48V at the master output. Parallel interconnection of masters is not supported by the software.
Feature descriptionThe battery is capable of powering a load and/or being charged via either power output (the outputs are connected in parallel internally). Using an integrated BMS, these outputs are regulated by a power semiconductor element. The state of charge is indicated on the LED indicator. The outputs are protected against short circuit by a 200A solid-state fuse (integrated).
Description of controls, inputs, outputs
Description of indicators
Single-phase off grid PV plant
Single-phase hybrid PV plant
Three-phase hybrid PV plant with communication
What do you need to purchase to make your own Single-phase off grid PV plant?
What do you need to purchase to make your own Single-phase hybrid PV plant?
What do you neeed to buy to make your own Three-phase hybrid PV plant with communication?
|The complet user manual and set up instructions can be found in Documets for download..|
|Nominal Voltage (V)||51.2|
|Max discharge current (A)||100|
|Optimal discharge current (A)||80|
|Max charging current (A)||100|
|Optimal charging current (A)||50|